The owner or operator of a gasoline service station required to install and operate a stage-one vapor recovery system shall comply with this part.
Stage-one vapor recovery systems must:
conform with the requirements of Design Criteria for Stage I Vapor Control Systems - Gasoline Service Stations as incorporated by reference in part 7011.0865;
incorporate a submerged fill pipe in each storage tank; and
The owner or operator of a gasoline service station with a vapor recovery system shall not accept gasoline without the vapor recovery system properly connected.
The owner or operator of a gasoline service station with stage-one vapor recovery shall:
maintain and operate the vapor recovery system in accordance with manufacturer's specifications;
promptly repair any malfunction of the system;
keep on the premises a copy of the manufacturer's operation and maintenance instructions and make these instructions available to the commissioner or an authorized representative of the commissioner on request; and
maintain system monitoring or testing devices in proper working order.
MS s 116.07
27 SR 1579
February 25, 2008