UPC section 903.1 is amended to read as follows:
903.1 Applicable Standards. Vent pipes and fittings shall comply with the applicable standards referenced in Table 701.1, except that:
(1) Galvanized steel or 304 stainless steel pipe shall not be installed underground and shall be not less than 6 inches (152 mm) aboveground.
(2) ABS and PVC DWV piping installations shall be in accordance with the applicable standards referenced in Table 1401.1.
40 SR 71
January 25, 2016
Official Publication of the State of Minnesota
Revisor of Statutes